The operation is controlled through the sequence programming by the energy saving system. When the dewpoint reaches at the specified temperature, a signal is fed back to step the reactivating process, and, several minutes before the dewpoint of outlet dry air becomes higher than the specified temperature, a signal is fed back again to restart the reactivation process. thus, the reactivation process suspending system considerable saves the purge air consumption incomparison with the usual continuous reactivating system.
|Working pressure||MAX 0.99MPa|
|Dewpoint||MAX －73℃ at Atomosphere|
|Swing cycle time||10min. / 5min.|
|Power source||AC100V 50/60Hz|
|Accessories||Control Panel, Pressure Gauge, Silencer|
|Option||Moisture Measurement, Flow Meter, Pre-Filter, After-Filter, Purge Air Saving System|